Solar heat gain coefficient (SHGC) by calorimeter method
|Measurement||Solar heat gain coefficient (SHGC), g-value|
|Standards||In addition to DIN EN 410 and DIN EN 13363-2|
|Measurement object||Glazings with shading systems or with more than 3 panes, high-scattering glazing, special components with integrated sun protection, domed building components (domed roof lights, membrane constructions), transparent specimens, vehicle constructions, screen printing or three-dimensional fabrics|
|Standard size and area of aperture||1 m², minimum of 0.5 m²|
|Test specimen dimensions||Minimum edge length 0.6 m, maximum of 2.9 m depending on construction|
|Test method||Nondestructive test method on special components, which are not included in above mentioned standards. This method is according to the latest state of technology but no normative standard yet.
The specimen is exposed to artificial solar radiation in the range 300 to 900 W/m². Then an energy balance is performed for the Hot Box behind the sample for defined environmental conditions.